2002 WTP Quarterly Report - 3rd Quarter
2002 WTP Quarterly Report - 3rd Quarter
12/1/2008 1:48:26 PM
2/21/2012 11:32:19 AM
General - Date
There are no annotations on this page.
Document management portal powered by Laserfiche WebLink 9 © 1998-2015
All rights reserved.
Page 1 of 1
Pages to print
Enter page numbers and/or page ranges separated by commas. For example, 1,3,5-12.
After downloading, print the document using a PDF reader (e.g. Adobe Reader).
Download electronic document
View plain text
Amherstburg Area Water Treatment Plant Quarterly Report Operated by the Ontario Clean Water Agency (OCWA) under contract to the Town of Amherstburg. For the period ending: September <br />30, 2002 Introduction This report is a summary of the last quarter's water quality, published in accordance with Ontario’s Drinking Water Protection Regulation. It includes important <br />information regarding the source of your water, analytical test results, and how it compares to standards set by the Province. If you have any questions regarding this report, please <br />contact our Client Services Representative listed in section 3 below. During this quarter, the Ontario Clean Water Agency (OCWA) conducted more than 102 tests for water quality parameters. <br />Of those tests, 3 samples were found to exceed the Ontario Drinking Water Standards as set out in Ontario Regulation 459/00 1 for Background Coliform and 2 for HPC. As a result we actively <br />undertook the following remedial actions of re-sampling flushing and a increase in distribution c?hlorine residual. Compliance With Provincial Regulations OCWA operates your water facility <br />in accordance with provincial regulations. Here is how we do it: ?? Use of Accredited Labs: Analytical tests to monitor your water quality are conducted by a laboratory audited by the <br />Canadian Association for Environmental Analytical Laboratories (CAEAL) and accredited by the Standards Council of Canada (SCC). Accreditation ensures that the laboratory has acceptable <br />laboratory protocols and test methods in place. It also requires the laboratory to provide evidence and assurances of the proficiency of the analysts performing the test methods. <br /> <br />Quarterly Report Page 2 ?? Operation by Licensed Operators: Your water treatment plant is operated and maintained by the OCWA’s competent and licensed staff. The mandatory licensing <br />program for operators of drinking water facilities in Ontario is regulated under the Ontario Water Resources Act (OWRA) Regulation 435/93. Licensing means that an individual meets the <br />education and experience requirements and has successfully passed the certificate exam. ?? Sampling and Analytical Requirements: OCWA follows a sampling and analysis schedule required <br />by OWRA Regulation 459/00, the Ontario drinking Water Standards. More information on sampling and analysis including results are available in this report and from your municipal office. <br />?? Adherence to Ministry Guidelines and Procedures: To ensure the protection of the public health and operational excellence, the OCWA adheres to the guidelines and procedures developed <br />by the Ministry of Environment and the Ministry of Health. System Information Facility Name: Amherstburg Water Treatment Plant Total Design Capacity: 18.184 (1000m3/day) Raw Water Source: <br />Detroit River Disinfection Method: Chlorine (gaseous) Municipal Location: Town of Amherstburg Service Area: Central/Western Area Service Population: 20,599 Client Services: Anthony Pizans <br />Phone Number: 519-344-7420 E-mail Address: email@example.com (A)Operations Manager: Chuck Fiddy Phone Number: 519-736-5447 E-mail Address: firstname.lastname@example.org Operational Description Pretreatment <br />Chemicals: Prechlorination (gaseous), Zebra mussel control Coagulation/Flocculation: Aluminum sulfate, Poly electrolytes Filtration: Anthracite, Dual Media Disinfection Method: Chlorine <br />(gaseous) Post Treatment Chemical Addition: Fluoride, chlorine (gas), Powdered Activated Carbon Waste effluent/residual Disposal: Direct to water course <br /> <br />Quarterly Report Page 3 Analytical Test Results Micro biological Parameters July August September Quarter Summary MAC /IMAC Total Coliform counts/100mls 0 1 0 1 0 Number of Samples 40 <br />32 32 102 Number of Detectable Results 0 1 0 1 Min /Max Exceedences Fecal Coliform counts/100mls 0 0 0 0 0 Number of Samples 40 32 32 102 Number of Detectable Results 0 0 0 0 Min /Max <br />Exceedences Heterotrophic Plate Count Number of Samples 15 12 12 39 Min /Max 0/47 0/2500 0/10 0/2500 500 Max Exceedences 0 3 0 3 Chlorine Residual Number of Samples 40 32 32 Min. Free <br />Dist. 0.13 0.06 0.2 0.05 Exceedences 0 0 0 0 Turbidity Number of Samples 180 184 179 Min/Max .01/.05 .01/.03 .01/.04 Exceedences 0 0 0 0 Typical Source of Contamination Microbial contaminants, <br />such as viruses and bacteria, may come from septic systems, agricultural livestock operations, wildlife, and wastewater treatment plants. <br /> <br />Quarterly Report Page 4 Comments: Two samples adverse HPC and one for Background. During follow-up sampling , during the Boil Water Advisory one sample tested positive for Total Coliforms. <br />All other samples and additional follow-up results were negative. Availability of Analytical Test Results The certificate of approval from the Ministry of the Environment, and Regulation <br />459/00 set out monitoring requirements for your water. The tables above summarize all the results required for inclusion in quarterly reports. Your water is extensively tested for the <br />presence of dozens of compounds. Some compounds, not listed above, may be present in low concentrations and their presence does not necessarily mean that the water poses a health risk. <br />Results of all analytical tests are available through your municipal office. Definitions and Abbreviations ?? MAC -Maximum Acceptable Concentration. ?? IMAC -Interim Maximum Acceptable <br />Concentration. ?? Coliform Bacteria -a group of commonly occurring rod shaped bacteria. Their presence in a water sample is indicative of inadequate filtration and/or disinfection. ?? <br />Fecal Coliform Bacteria -refers to a subgroup of coliform bacteria present in the digestive system of warm blooded animals and humans. ?? Heterotrophic Plate Count -a method of measuring <br />bacterial content in water samples. Also known as Standard Plate Count. ?? Organic Parameter -a group of chemical compounds containing carbon. ?? Inorganic Parameter -a group of chemical <br />compounds not containing carbon. ?? Raw Water -Surface or ground water available as a source of drinking water that has not received any treatment. <br /> <br />
The URL can be used to link to this page
Your browser does not support the video tag.